A downloadable PDF of this blog post is available here.
Demand for on-farm cold storage of produce is increasing as local markets for these goods expand. Many local producers are asking about CoolBots™, a tool that works with a window air-conditioner to make a cooler out of an insulated space. This article collects information about CoolBots and highlights some considerations growers should be aware of.
Why use a CoolBot?
CoolBots cost less to install than a traditional refrigeration system. They can be installed by anyone with basic mechanical skills. The maintenance is also something that can be done by most people with basic skills.
In a nutshell
- Understand your storage needs;
- How much of each crop is being stored? How much space is needed for each crop?
- Target temperature and humidity for each crop or group (see USDA Handbook 66 and UVM Crop Storage Planner)
- Cooler size (UVM Crop Storage Planner)
- How often will you be opening the cooler door? How can you reduce that?
- How will you remove field heat prior to storage?
- Build a good cooler box (room)
- Understand the limitations of the CoolBot
- Use a recommended AC unit of appropriate size
- Plan for maintenance (cleaning the air conditioner coil, off-season storage, protection from elements, clearing the drain pan and drain hole, etc.)
- Maintenance and troubleshooting guides are available from storeitcold.com
Many vegetable farmers utilize Coolbots ($349), a controller that allows the AC unit to run with a lower temperature than normal, to simplify the refrigeration system of their walk-in coolers.
Store It Cold, the manufacturer, has a website with excellent resources and FAQ’s,including a list of recommended AC units.
CoolBots are NOT recommended for:
- Rapidly cooling a product
- As a freezer – CoolBots perform best above 36 °F and will not go below 32 °F.
- Sites with many door openings per day (for example > 6 times per hour)
- Running through the winter – not a show stopper, but you need to be more careful about which AC unit you choose
Other things to be very aware of, according to the CoolBot controller manufacturer, include
- A well-constructed cooler box – Start with a well-insulated (>R24), well sealed (caulk and spray-foam everything, no gaps) cooler box. The University of Kentucky has an excellent set of documentation, and presentation for a low cost cooler design. North Carolina State University also has a fact sheet with guidance on cooler sizing and construction.
- A well-suited AC unit – avoid portable AC units. The AC unit will need to have a digital display and automatic restart.
- Cooling a space above 61 °F.
Cooler Cleaning Checklist
Whether your winter storage rooms are getting bare or you are making the transition from sweet corn to potatoes, what better time to do a good cleaning and even sanitizing than now?
Download this Guide & Checklist as a PDF or read more in the blog post: Spring Cleaning – Farm Cooler Checklist
Comments are closed.